Sometimes it’s essential that you completely drain your school’s indoor pool. In our case, the pool needs to be drained so that workmen can erect scaffolding, to replace the swimming pool lighting. This guide is not the same as an outdoor pool winter closing down procedure, as we will be completely emptying the pool of water. Winterising involves blowing out the return pipes and emptying the sand filter. Neither are needed in this case.
The first job is to use your pool net to remove any objects that may be in the pool. I would also recommend using your pool vac, to clean the bottom of the pool before we empty it. Next, I removed the baskets from the pool skimmers. removing the baskets isn’t mandatory but I removed them anyway. Our next thing to do is to work in the plant room, to physically drain as much of the water as possible. This uses the floor drain in the deep end of the pool.
OK, now we are in the Plant Room, where all the tech that keeps the pool in order is kept. Most pool Plant Rooms look a bit like the image below. It is the beating heart of the pool, cleaning and maintaining the water, 24 hours a day. The Plant Room usually has the pump, the large sand filters, the heater and alot of pipework.
Our first job is to shut down the heater. Depending how your system heats the water will depend on how you shut your heating system off. Ours is gas, so as well as switching off the heating system, I also switched off the gas isolation cock as well. As we are working on a indoor pool, which won’t be empty for long, (about a week) there is no need to drain down the boiler. Now we can get the pool emptied.
Now go to your pump and at the side of it, you need to close the valve to the return pipe for the pool. You will also need to open the drain valve for the pool as well. In our case, the swimming pool drain goes into the main drains, so we do not need to connect a hose.
Your pump should have a setting called “drain”, you need to turn the controller on the pump to this position, to drain the pool. If your pump does not have a drain setting, switch it to “backwash” instead. I also opened the inspection chambers as well to make sure the pool is draining correctly. any water left in the return pipes will drain out into the pool, during this process. The water level should now of completely dropped, but there may be some residue of water around the drain. I use a hard brush to make this go down the drain, once the cover is removed. Now go back to your plant room, switch off the pump, close the drain cock. The pool return valve should remain closed, to prevent water from the filter entering the pool while work is carried out. I also Lockout-Tagout the main switch for the plant room, to prevent anyone switching on the power to the plant room, while the pool is empty.
Finally, I have put a sign on the doors to the pool area, saying that the pool is closed. As entry to the pool is via PACS System, I used a chain around the handles of the door and attached a padlock, to make sure no one can get in, while the pool is out of use.
And that’s it, one emptied pool. Once the work is completed, (in 1 – 2 weeks time) I will do a guide on filling and setting up the pool.